This section of the site includes our webinars, onesheets, manuals and more. Simply navigate to the desired literature or video and click to expand the section.
Hydronic heating is an energy efficient system that uses tubing to run a hot liquid beneath the floor, along base board heaters, or through radiators to heat your home. Also referred to as radiant heating, this type of system has become increasingly popular among families that want added comfort and control in their heating zones, savings through lower heating bills, and a smaller carbon footprint. It operates by pumping hot water, or alternative heated liquid through loops of plastic piping. These pipes are installed within your homes concrete slab or floor joist system and allow the heat to radiate evenly across the entire floor surface.
The liquid in a hydronic system begins in a boiler, where it is heated before flowing to a plumbing manifold. Your plumbing manifold acts as the control center by connecting to a thermostat and directing the correct temperature of water to the various heating zones of your home. This allows each zone to maintain a personalized, steady temperature. Pumps work to constantly circulate newly heated water into the tubing, while cooler water is returned to the boiler to begin its journey again.
This closed loop system of heating allows for flexible temperature customization, while maintaining an incredible level of energy efficiency.
Hydronic heating provides superior comfort because the entire floor radiates heat up from the ground in an even and consistent manner. Traditional forced air systems work by blowing warm air through a series of duct work in the floors, walls, and ceilings, and out by way of one or two vents in a room. This method can lead to hot and cold spots due to poor air circulation, as well as temperature spikes and dips when the system turns on and off. It can also disturb allergens and circulate dust throughout your home. Under floor hydronic systems eliminate this issue by producing a steady heat that radiates from the floor throughout the entire room, without disturbing dust or allergens.
HBX is made up of several industry veterans from the Automation, HVAC and Electronics industries. This combined talent has developed a plethora of controls for a multitude of commercial, industrial and residential heating and cooling management applications. Technical know-how in conjunction with real-world experience have been applied to the design, construction and installation process of our controls. From complex, expandable hydronic controls, to our advanced P.I.D. Thermostats, HBX has every component for your Heating Project.
Designing your hydronic heating system to function with multiple boiler stages by switching on/off multiple smaller capacity boilers will save money, energy, limit potential wear and tear and add a higher degree of comfort to your building.
Large heating loads supplied by one or two very large boilers typically don't make sense when the heating plants full capacity may only be required for 5-15% of the entire year. A smaller boiler may keep up with the demand 50% of the time in most cases. Staging controls allow you to take full advantage of the benefits derived from a series of smaller boilers/stages cycled on as the heating load dictates. Overshoot and undershooting of desired room temperature can be reduced, while saving money.
Multiple boilers provide an inherent backup in the event of a boiler failure. Quality staging controls also allow for automatic rotation of all boilers with various options to equalize runtime. download drawings (ZIP - 186 files)
Hi-temp boiler supply water can be mixed with a lower temp distribution system. Valves or pumps can be used to temper the distribution system water temp. As part of a closed loop system the mixing valve or injection pump is designed to divert a calculated amount of hot water into the distribution system, at the same time the distribution system gives up the same amount of returning cooler water back to the boiler side to be re-heated and re-circulated. Thermistors in the boiler and distribution loops provide feedback to the Control, which regulates the distribution water temp.
Large distribution loops can return very cold temperatures back to the boiler. If unabated, this cold water creates condensation in the flue. This condensation mixed with exhaust from the combustion process creates sulphuric acid, corroding metallic components in its path. High temperatures released from the boiler may crack concrete and warp floor coverings such as hardwood. Correctly installed mixing systems compensate for this. download drawings (ZIP - 40 files)
Larger commercial and industrial users often choose to run independent boiler systems from the existing space heating boiler system. Several advantages support the theory of independent boiler plants/systems.
Dedicated DHW loads can be sized to optimize the efficiency with boiler selection options. Options exist to use potable water through the boiler as would apply to direct forced systems, and eliminate the potential for internal ingress of glycol through heat exchangers. DHW systems tend to exhibit both very large temperature drops and very subtle temperature drops depending on time-of-day and usage. Short cycling of boilers and pumps can be problematic which may lead to large overshoot or undershooting of target temperatures. download drawings (ZIP - 8 files)
The principle of the Dual System ID Card is to control 2 traditionally separate boiler staging applications via one controller:
The Dual Mixing application will allow for mixing capabilities in multi-family dwelling applications (and certain industrial buildings). Two separate mixing systems (ie. In-joist heating and in-slab heating) are able to be controlled via a single HBX Control, giving each independent heating characteristics. download drawings (ZIP - 4 files)
Solar energy is the most abundant energy resource in the world. Every day, more sunlight is available than the world can use for all of its energy needs. Collecting the sun's clean energy and transforming it into practical forms of heating is the focus of the rapidly growing solar energy industry. Optimizing the control strategy in a solar system is key for achieving optimum BTU return. Whether utilizing solar panels or solar tubes, the ECO-1000 can improve tanks, pumps and panels in the system to draw maximum heat from the solar devices; thus increasing efficiency and effectiveness of your solar application.
A multiple tank feature provides you with the ability to run numerous storage tanks simultaneously, allowing for the added benefits of continuously keeping the lead tank as hot as desired. As well as a backup feature, the ECO-1000 Control has the advantage of controlling overheated occurrences by turning on a pump or valve to dump/shed excess heat from panel or tank. download drawings (ZIP - 38 files)
The earth's temperature a few meters below the ground is relatively constant everywhere in North America while the air temperature can change from summer to winter extremes. Geothermal heat pumps combined with a dedicated geothermal control (ECO-1000) can tap into this natural heat source and provide a positive energy return to your residential, commercial and industrial applications.
The HBX Control Systems ECO-1000 will allow you to take advantage of the benefits derived using outdoor reset to improve compressor efficiency. The ECO-1000 control combined with the Computer Interface Software (CIS) allow for features such as monitoring and troubleshooting parameters accessible to the installers/end-users with simple but sophisticated fine tuning characteristics. download drawings (ZIP - 28 files)
We can be reached via e-mail here or you can reach us by telephone at (403)720-0029
For each visitor to our website, our web server automatically recognizes only the consumer's domain name, but not the e-mail address (where possible). We collect the e-mail addresses of those who communicate with us via e-mail, aggregate information on what pages consumers access or visit, user-specific information on what pages consumers access or visit, information volunteered by the consumer, such as survey information and/or site registrations, name and address, telephone number, fax number. The information we collect is used to improve the content of our website, used to customize the content and/or layout of our pages for each individual visitor.
If you supply us with your postal address online you will only receive the information for which you provided your address. Persons who supply us with their telephone numbers online will only receive telephone contact regarding the services or information for which it was provided.
If you do not want to receive e-mail from us in the future please contact us. Please provide us with your name and phone number. We will be sure your name is removed from the list we share with other organizations. With respect to Ad Servers: We do not partner with or have special relationships with any ad server companies.
From time to time, we may use customer information for new, unanticipated uses not previously disclosed in our privacy notice. If our information practices change at some time in the future we will post the policy changes to our website to notify you of these changes and provide you with the ability to opt out of these new uses. If you are concerned about how your information is used, you should check back at our website periodically. Customers may prevent their information from being used for purposes other than those for which it was originally collected by e-mailing us here. Upon request we provide site visitors with access to a description of information that we maintain about them. Consumers can have this information corrected by calling us at (403)720-0029.
With respect to security: We have appropriate security measures in place in our physical facilities to protect against the loss, misuse or alteration of information that we have collected from you at our site. If you feel that this site is not following its stated information policy, you may contact us at the above addresses or phone number.